AEIC CS Specifications for Thermoplastic and Crosslinked Polyethylene Insulated Shielded Power Cables Rated 5 through 35 kV, 9th Edition, AEIC CS, Specification for Impregnated Paper and Laminated Paper AEIC CS, Specifications for Cross-linked Polyethylene. AEIC CS, Specifications for Crosslinked Polyethylene Insulated . aFor use with % insulation level cable as defined in AEIC CS or AEIC CS
|Published (Last):||6 June 2005|
|PDF File Size:||11.94 Mb|
|ePub File Size:||7.10 Mb|
|Price:||Free* [*Free Regsitration Required]|
All ingredients shall be mixed through an appropriate screen pack and then.
However, both the pseudoglow discharges irrespective of the length of their rise time as well as pulseless glow can be readily measured either by Method A or B of Test Methods D Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard. We’re encouraging our customers to include them in the purchasing process.
Quadruplex volt secondary underground distribution cable; “EC” grade aluminum hard drawn conductor in accordance with ASTM B; Class B standing in accordance with ASTM B; Insulation shall be cross-linked polyethylene with minimum average thickness of 78 mils. It is possible that such partially conducting surfaces will develop with polymers that are exposed to partial discharges for sufficiently long periods to accumulate acidic degradation products. Size and type of cable d. Ware concludes, “Overall, we feel it’s in the best interest of the utility industry to move to the new standards.
The City of Ocala is looking to purchase the following items: Cable spec clarification letter. Bidders can be approved by contacting Mary Ann St. You have to check your accessories to see if they will accept the smaller diameters. In most of the applications, it’s not a problem.
Aekc and type of cable. In the new MV standards scheme, the requirements are very similar, but they’re organized by cable architecture. Phase conductor shall be stranded aluminum with cross-Linked Polyethelene Insulation. Association of Edison Illuminating. New Numbers To Know Medium-voltage cable buyers encountering familiar cable requirements transformed into ANSI standards If you’re shopping for medium-voltage cable, some very familiar aec are about to change – and you’ll need to learn some new numbers.
Maximum reel diameter to be 66″. Medium-voltage cable buyers encountering familiar cable requirements transformed into ANSI standards.
Historical Version s – view previous versions of standard. Medium-voltage cable buyers encountering familiar cable requirements transformed into ANSI standards Specifying Cable?
These tests shall include the electrical and thermomechanical. These specifications describe a 3 conductor, neutral supported, service drop cable rated at volts and consisting of two insulated aluminum conductors twisted around a bare neutral conductor further specified below. City of Ocala, Central purchasing. A waterproof tag shall be firmly affixed to each reel having the following information: It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
Also in some applications, like turbogenerators, where xeic low molecular weight gas such as hydrogen is used as a coolant, it is possible that pseudoglow discharges will develop.
The utility industry’s long-standing requirements for cross-linked polyethylene XLP and ethylene propylene rubber EPR MV cable insulations have been combined into a single document that has been accepted by the American National Standards Institute. If you’re shopping for medium-voltage cable, some very familiar requirements are about to change – and you’ll need to learn some new numbers.
Link to Active This link will always route to the current Active version of the standard. If the rise times of the pseudoglow discharges are too longthey will evade detection by pulse detectors as awic in Test Method D Fs5 of shield in. Specific precaution statements are given in Section 7.
However, if there are numerous discharges per cycle it is occasionally important to know their charge sum, since this sum can be related to the total volume of internal gas spaces that are discharging, if it is assumed that the gas cavities are simple capacitances in series with the capacitances of the solid dielectrics 7 8. Reference must be made to City of Ocala purchase order number, quantity, and weight of. Some overall diameters are different.
Therefore, foreign-based manufacturers will need to supply documentation that clearly shows that the cable is made in the USA. Length of cable e. YES designates that the cable shall be marked with sequential footage markers for the entire length of the cable. Joint task force drafted new standards.
Reel Gross, tare, and net weight. Triplexed volt secondary underground distribution cable; “EC” grade aluminum hard drawn conductor in accordance with ASTM B; Class B standing in accordance with ASTM B; Insulation shall be cross-linked polyethylene with minimum average thickness of 78 mils.
Neutral conductor shall be Bare stranded ACSR aluminum, and of equivalent size of the insulated conductors.